After an API 653 inspection, any tank bottom damage must be repaired to API 653 standards. Whether the damage is in a small area or is widespread, PTS will evaluate the inspection report and create a timely, cost-effective repair plan to meet API 653 and owner-provided specifications.
Tank Double Bottom / El Segundo Repair
Many tanks are mandated to add leak detection and secondary containment when tank inspection dates are reached. Double bottom tanks are recognized by API and the U.S. Environmental Protection Agency as an effective release prevention barrier (RPB), a type of secondary containment. A double bottom repair uses a new steel bottom on top of the existing steel bottom, separated by an impermeable liner and concrete. The separating material can also be sand with cathodic protection embedded. Slots or grooves in the concrete allow the tank operator to monitor for leaks. This design is also known also known as an El Segundo tank bottom.
Tank Bottom Corrosion Repair
For tanks with slight bottom plate corrosion, our knowledgeable crews will be able to add patch plates or puddle weld corrosion to quickly return the tank to service.
Tank Annular Ring Repair
A faulty annular ring can be dangerous. Tank bottom corrosion that is limited to the perimeter of the tank will require an annular ring repair. Our engineers will diagnose the damaged tank annular ring and coordinate with our tank repair crew to keep your above-ground tank remains leak-free.
Tank Chime Sealing
Do not let water under your tank! Our field crew will seal your tank chime to ensure the tank bottom remains sealed for years to come to protect the tank chime and tank bottom from corrosion.
Tank Chime Corrosion Repair
Our technicians will diagnose and eliminate any tank chime corrosion issues at their source, thoroughly repair any corrosive damage to the chime, and seal it to prevent future corrosion.